for McLean, VA
Steven - McLean, VA
Joe - McLean, VA
Michael was an excellent technician. We had to do some detective work to be able to make the repair and we got a difficult and messy job done in half a day. He was mindful of the fact that we had customers in the building and did everything he could to minimize his impact on their experience. We appreciate it.
1 - McLean, VA
Amadou - McLean, VA
in and out
Tim - McLean, VA
Great service, professional tech
Jim - McLean, VA
The technician, Dave, was on time, professional, and efficient. He conducted our semi-annual kitchen fire suppression system maintenance check up with a smile. He also pointed out a potential issue with the position of our stove. We had moved it a few inches to make room for a side table, but in doing so, we moved it out of the ideal position for the suppression spray to cover the whole unit. Thanks Dave for taking the extra step to ensure our safety.
service on fire marshal inspection
Mary Ann - McLean, VA
He was knowledgeable and polite, while waiting on the fire marshal, he did his inspection in order to maximize the use of his time.
Tonia 9-10a MUST SEE BRIAN OR AUDREY. THEY ARE MEETING YOU. Portable Extinguishers and Emergency / Exit Lights Inspection ***NEW CONTRACT BEGAN 04/2022*** Annual Extinguisher Inspection Equip Desc: (6) Extinguishers ***NEW CONTRACT BEGAN 04/2022*** Annual Lights Inspection Equip Desc: (6) Emergency/Exit Lights Inoperable Deficiency: Emergency light 2nd floor hallway by bathrooms Bad charging board and needs replacement Emergency light 2nd floor hallway by filing cabinets Bad light needs to be replaced Inoperable Deficiency: (2) New 5lb abc extinguisher needs to be installed ** Admen office 2nd floor rear exit to roof top & exit to stairway ** New 5lb abc extinguisher needs to be installed inside storage area By employee entrance New 5lb abc extinguisher needs to be installed Employee entrance New 5lb abc extinguisher needs to installed (optical hallway) New 5lb abc extinguisher needs to be installed Emergency exit to parking lot **NOTE 3 (2.5 gallon abc extinguishers) we
john 571 225 8035 730-8a Portable Extinguishers Inspection Annual Inspection Dept: EXTING Equip Desc: (27) EXTINGUISHERS Inoperable Deficiency: (1) 5 lb Clean Guard extinguisher due for 6 year service Deficiency for 5 lb CO2 Storage & meter room: 10lb co2 extinguishers are due for hydro x2 2 10lb abc extinguishers are due for hydro testing Deficiency for 5 lb ABC Front door: 5lb abc extinguisher is due for hydro testing Last 6 year maintenance was performed in 2013 Deficiency: Number of Extinguishers Left at Job: 1